Status: Complete and approved by customer.
Pimp stations #1-4 detailed survey.
Condition check of
- suction chambers and pipelines
- ramps and ladders
- stoplogs and their guidelines.
Sludge setting measurement. Inspecton of armored concrete structures.
Power pools #1 and #2 survey.
Inspection of fish protection structures and thrash-rack water intakes.
All obectives was completed. A number of anomalies (concrete cracks, damaged metal elements, abnormal elements wear etc.) was found. Detailed report was submited to the customer.